Detector re-alarms – reducing the riskDetector re-alarms – reducing the risk https://www.detectortesters.com/wp-content/uploads/2018/07/Detector_Re-alarms.-Reducing-the-risk-780-x-488px.jpg 780 488 Detector Testers Detector Testers https://www.detectortesters.com/wp-content/uploads/2018/07/Detector_Re-alarms.-Reducing-the-risk-780-x-488px.jpg
- no comments
Detector testing is sometimes slowed down by nuisance re-alarms. Re-alarms occur when the ‘smoke’ used to test the detector remains around the sensor causing the detector to re-alarm.
In a recent twitter poll, 60% of respondents told us they experience re-alarms when testing. This obviously extends the time spent testing and can lead to greater disruption around site.
Typically, re-alarms are most common when testing with a smoke aerosol can – when the application of smoke to the detector can be over-applied. So, what can be done to reduce the risk of re-alarming detectors?
- If you are using a dispenser, ensure the smoke aerosol is compatible. The Solo 330 is designed to work only with the Solo range of smoke aerosols, other aerosols may appear to work – but their design and the way they discharge spray is not compatible with the Solo 330
- When using the Solo 330 dispenser and Solo smoke aerosol – ensure the right amount of ‘smoke’ is used. A short one second burst is all that is needed to operate the majority of detectors – over application doesn’t lead to faster testing
- If you are using a hand-held aerosol, ensure you are not too close to the detector. The best way to ensure this is to use SmokeSabre where the built-in ‘sabre’ prevents use too close to the detector.
In recent years, more modern forms of testing have been developed which include a built-in ‘clearing’ cycle. These cycles clear the detector of smoke after testing ensuring the detector doesn’t go back into alarm.
Both Testifire and Solo 365 generate smoke on-demand, meaning that smoke is only generated whilst the detector is within the test cup. This helps ensure only the amount of smoke needed to activate the detector is used – which in turn helps reduce the risk of re-alarms. If a re-alarm does occur using Testifire or Solo 365 the ‘clearing’ function can be used immediately after testing to clear the ‘smoke’ away from the detector.
Stay updated – sign up for our newsletter!
We are committed to protecting your privacy.
The information that you have supplied will be used by us to keep you up to date with news, exhibitions, events, training and special offers. We will not share your details with any other company or institution.
Once registered you will have the opportunity to update your preferences and contact details.
You might also like
The smarter way to test smoke detectorsThe smarter way to test smoke detectors https://www.detectortesters.com/wp-content/uploads/2020/06/Solo-365_Product-Focus_2020-780-x-488px.jpg 780 488 Detector Testers Detector Testers https://www.detectortesters.com/wp-content/uploads/2020/06/Solo-365_Product-Focus_2020-780-x-488px.jpg